The basic material of KSZ36-25-1600 kVA transformer substation is concrete complying with electrical, thermal and mechanical requirements set out in MSZ EN 62271-202:2014 standard specifications. The transformer substation is monolithically cast as a single piece one, built without gap. The compression strength of concrete conforms to Grade C30/37. The transformer substation consists of three compartments, namely a medium voltage switchgear compartment, a transformer compartment and a low voltage switchgear compartment. The medium voltage switchgear compartment allows to install SF6 gas insulated switchgear units and an air insulated measuring cell. The transformer compartment formed inside the substation allows to install a transformer with a rated power of up to 1600 kVA.
Main technical specifications:
|Maximum voltage:||24 kV|
|Medium voltage side, rated thermal short time withstand current:||16 kA/1s|
|Rated current:||630 A|
|Substation protection degree:||IP 23D|
|Maximum transformer power:||1600 kVA|
|Low voltage busbar rated current:||2500 A|
|Low voltage power infeed main device:||Circuit breaker, disconnector, switch|
|Low voltage branchlines:||NH00, NH1, NH2, NH3|
|Low voltage distribution unit protection degree:||IP2X|
|Medium voltage side, cable entries:||watertight (Hauff system)|
|Low voltage side, cable entries:||not watertight (upon request sealed cable entries can be installed)|
|External finish of concrete:||patent plaster (colour selectable according to RAL scale of colours)|
|Width:||2 550 mm|
|Length:||3 600 mm|
|Height:||2 720 mm|
|Basic area:||9,18 m2|
|Weight:||14 000 kg|
|Roof overhang size:||100 mm around the substation|
Product standard relevant to the substation: MSZ EN 62271-202:2014 High voltage switchgear and controlgear units. Part 202: High- / low voltage pre-assembled substation.
For further information please contact us!